View and Download Regin CORRIGO L10 manual online. CORRIGO L10 Controller pdf manual download. Click to download: >>> Download regin corrigo l10 manual >> Download songs computer memory card corrigo l10 manual. Corrigo design ergonomic chair, back pain, posture correction, office chair. EUR ; 0 bids; + EUR postage. 4d 11h left (Tuesday, ).
|Published (Last):||20 December 2008|
|PDF File Size:||8.75 Mb|
|ePub File Size:||14.16 Mb|
|Price:||Free* [*Free Regsitration Required]|
regin corrigo l10 manual – lietinkplanab’s blog
It has been designed for use in less complex air-handling systems. The controller has a display and built in indicator on the front for xorrigo and is operated by means of clearly defined buttons. The AI4 input is used as a digital input l01 the unit is configured with overheat protection on an electric heater.
In that case, connect this input to a poten- tial free closing contact. Reference point is terminal 23, cortigo neutral which is internally connected to terminal 25, system neutral. AO3 make up the temperature controlling sequence. Function for each output is determined by configuration setting but the order is always Y3? Y1 on increasing heat demand. Operating buttons Up arrow – scrolls upwards in menu selections. If the key is held in depressed position it will repeat. Down arrow – scrolls downwards in menu selections.
The display alternates between a general display with product description and Menu information If the user attempts to make changes that cannot be cirrigo or which lie outside his user level the controller will display the following information: Unauthorized No changes in Make new logon this menu Alarms When alarms are activated they are displayed in the alarm queue and also as a flashing red light on the display panel on the front of the controller in the event of an alarm.
REGIN CORRIGO L10-LON
Should the code for level three be corrugo the sys- Important! This code number is time limited. Automatic restart after changing When one or more coreigo have been changed the controller will restart when the user leaves the configuration menu.
Used for resetting unit to factory settings Not part of the configuration code. Configuration Supply air control with outdoor temperature compensation Supply air control with outdoor temperature The temperature sensor Supply Air AI3 controls the sequences to reach setpoint.
The setpoint is compensated with respect to the temperature at outdoor temperature sensor AI1. The temperature at the Supply air sensor AI3 is kept within the minimum and maximum limits set.
Regin CORRIGO L10 Manual
The sequence or- der, however, is always the same: Temperature At increasing heat requirement Y3 is always activated first, then Y2 and finally Y1. Configuration Controlling plate heat exchanger Plate heat exchanger means that the output controls e.
Defrosting plate heat exchanger Ice-build up sensor pressure switch is connected to DI4. On ice build-up the defrosting function is activated. DI1 has to be closed. If no status running signal is present at DI1 after a preset delay time, a fan alarm is activated and the system stops.
Factory settings Basic setting Use this option to return Corrigo L10 to factory setting. If you enter the? Outdoor temperature or external setpoint Room temperature Supply air temperature Frost protection sensor When frostprotection is selected with water heater or Overheat protection When electric heater is used DI1 Fan malfunction or fan status indicator. Outputs Shows present values for AO Outputs can be set manually.
This requires user level 1. Scheduler L10 has a scheduler based on a one-week period. The scheduler can handle power losses for at least 24 hours without loss of data. Settings All parameter settings have been gathered under this menu. Explanation of control Which parameters are shown or hidden depends on which control function has been funktions selected.
Supply air control 1. Supply air control with 1. Settings – continued Outdoor compensation, breakpoint 1. Control function 1, 5.
Outdoor compensation Values for compensation can be freely set but the breakpoints should be ordered with the highest highest outdoor temp at 4 and lowest lowest outdoor temp at 1.
Important alarms however, such as frostprotection, overheat protection and smoke alarms always activates the alarm output and will not be affected by this setting. Commissioning protocol Site System Date Commissioned by: Pg 1 No value written means default value Configuration Default setting Actual setting Config code Supply air control with outdoor temperature compensation 2.
Room control with cascaded supply air temperature control 3. Page of 30 Go. L10 is a new controller which has been designed to be easy to use and.
The controller has been designed for mounting on a DIN rail, in norm housing or on. The required functions are selected with the help of questions in normal script or by. The menu system works with different user-levels to 1l0 settings and to allow.
This means that non-technical staff can feel secure while. During normal operation, without pressing any buttons, the display also shows the.
L10 for use with air handling systems comes with or without LON. Table of Contents Add to my manuals Add.
Controllers for heating, boiler and ventilation applications in buildings. Page 8 Operating buttons Up arrow – scrolls upwards in menu selections. Settings Menu information If the user attempts to make changes that cannot be made or which lie outside his user level the controller will display the following information: Table Of Contents Automatic restart after changing When one or more parameters have been changed the controller will restart when the user leaves the configuration menu.
Y1 Automatic Reset Configuration Controlling plate heat exchanger Plate heat exchanger means that the output controls e. Page 21 Outputs Shows present values for AO Page 22 Scheduler L10 has a scheduler based on a one-week period.
Page 23 Settings All parameter settings have been gathered under this menu. Page 24 Settings – continued Comments to this Manuals Your Name. Enter text from picture: By pressing ‘print’ button you will print only current page. To print the manual completely, please, download it. Don’t show me this message again. Got it, continue to print. Don’t have an account?